|SIM / KS 94 and SIM / KS 98
Standard signals at the inputs
The analog inputs of the simulations normally expect a technical value. With
thermocouple inputs, the entry "458" represents a temperature of 458 0 C. If the input is configured as a
standard signal, a technical value is also expected. However, it is also possible to simulate a current signal, in
order to check the selected scaling range. For this, the entered value must be preceded by '#'.
The input is configured for 4...20 mA, with x0=200, x100=800.
Entered value: #4
The value 4 mA is converted to 200, according to the scaling.
Entered value: #20
The value 20 mA is converted to 800, according to the scaling.
Copyright © 2001 PMA Prozeß- und Maschinen-Automation